KSB HGC 31-3 3-Stage Boiler Feed Water
This photo shows the final assembly of a refurbished Model HGC KSB Boiler Feed Water Pump. In service at a power plant, this pump required new components which Hydro South manufactured in-house. Hydro can offer upgrades and modifications for KSB pumps to improve performance and reliability.
Ingersoll Rand 43 APM Vertical Pump
The Ingersoll Rand 43 APM vertical pump shown above operates at a power plant in a circulating water application. Hydro repaired the cracked impeller and re-established proper fits and tolerances.
KSB HGC 5-8 Boiler Feed Water
On-site technical support for power industry. Boiler Feed Water. Support user with interpretation and root cause of severe vibration values. Pump was tripping shut down caused by system valves.
Baldwin Lima Hamilton Circulating Water
Shown above is the precision balancing of a 3000-pound impeller-shaft assembly for a Baldwin Lima Hamilton (BLH) circulating water pump prior to final assembly. The vane angles are precision-machined to match stationary liner, which minimizes leakage, increases efficiency and extends mtbr.
Byron Jackson Vertical Condensate 24KXHO
The photo above shows the curved bowl in a vertical pump for the power industry.
Sulzer MSDD 6x10x12.5 2-stage
This Sulzer MSDD heater drain pump, which operated in a power plant, had been experiencing leaky seals and a change in performance. Hydro South restored the impeller and case rings to regain performance. New bushings were also installed to eliminate leaks.
Ingersoll Rand 2 CNTA 6-Stage Boiler Feed
The picture above shows the Boiler Feed Pump being prepared for final shipping. Final settings begin the movement from assembly to shipping preparation.
IDP 2.5 CNTA 8-Stage Boiler Feed Pump
This high-pressure feedwater pump, which was utilized by a brewing company, was sent to Hydro South to be refurbished. Hydro South manufactured and installed new internal rings and assembled to proper tolerances to restore this pump for service.
Bingham 12x16x23 CDB Centrifugal Pump
Refinery pump being repaired due to abrasive debris causing damage to the rotating parts. New casing rings provide the allowed clearance for operation.